We are operating at reduced capacity due to COVID-19 Alert Level Three restrictions. Please only call our 0800 number if someone is at serious risk of harm or has been seriously injured, become seriously ill, or died as a result of work.
For other notifications please complete our online forms at Notify WorkSafe.
Energy Safety’s investigation determined that a Metering Technician replaced a revenue meter while it was still live. In doing so, while attempting to terminate the last phase conductor into the new revenue meter terminals, a short circuit was created causing considerable damage to the metering panel and minor burn injuries to the technician’s left hand that required medical attention.
Energy Safety considers the company replacing the meter potentially failed to take all practicable steps under the Electricity Act and Regulations. The company provided an employee, or a contractor, a choice to work live in their "Low Voltages Live Work Process – Meter Change" procedure rather than starting with the premise that live work should be avoided.
Energy Safety notes that when replacing a whole current meter the power is going to be interrupted to the installation and therefore there is no foreseeable reason to permit this work to be carried out live.
Energy Safety noted and advised the company that there were a number of omissions within the procedure for live work.
Energy Safety recommended that the company withdraw this procedure and provide alternative methods of disconnection, such as the removal of pole fuses by an approved competent worker, for any work that does not have readily accessible disconnection device.
Energy Safety concluded there were potential breaches of the Electrical (Safety) Regulations 2010 specifically regulation 16 & regulation 101 and a potential offence under section 163C (1) of the Electricity Act 1992. This matter has been referred to the compliance officer for consideration.